1: DC 12V (12V Version), DC 24V (24V Version) (optional)
2: Standby current (DC 12V all relays closed) 14MA, 1 relay open 41MA, 2 relays open 69MA, 3 relays open 95MA,4 relays open 122MA,5 relays open 149MA,6 relays open 174MA, 7 relays open 198MA,8 relays open 226MA
3: 12 photoelectric isolation Input ports (NPN low level active ), the input and output relationship can be set to associated (default) and non-associated through commands.
4: ”open” ”close” ”Momentary” ”Self-locking” ”Interlock” ”Delay” ””Interlock between two channels” 7 Commands
5: MODBUS RTU command, Support 03 06 16 function code
6: Under the ”Delay” command ,the maximum delay is 255 seconds;
7: MODBUS commands can be made serial HyperTerminal (serial assistant) OR ”Modbus Poll” Enter;
8: Under the MODBUS command mode, it can support up to 64 devices in parallel
9: The default baud rate is 9600BPS. The baud rate can be selected through jumpers: 2400 4800 9600 19200 38400 57600 115200BPS
10: The check methods can be none parity check, even parity check and odd parity check
11: The data sending and returning time can be set, with a maximum value of 1000ms
12: Size: 200 * 72 * 22mm(Only PCB Board);220 * 88* 46mm(with Din Rail Box)
13: Weight: 250.5g(Only PCB Board);382g(with Din Rail Box)
14: Maximum load: 10A / 250VAC, 10A / 125VAC, 10A / 30VDC, 10A / 28VDC, 10A / 12VDC
DIN rail Box parameters:
Product model: UM72
Width: suitable for PCB board width UM72(72mm)
Insulation grade: flame-retardant VO grade
Backplane length: suitable for 200 mm PCB boards
Installation: DIN35 and C45 rail
NO: Relay normally open contact
COM: Relay common contact
NC: Relay normally closed contact
Open: NO connection COM, NC disconnect COM
Close: NO disconnect COM, NC connection COM
Momentary: Enter the Momentary command, the Rreceiver Relay is Open, delay of 0.5 seconds after, Relay is Close;
Toggle: Enter the Toggle command, the Rreceiver Relay is Open, Enter the Toggle command again, Relay is Close;
Latched: Enter the Channel 1 Latched command, the receiver Channel 1 is Open, the Channel 2 is Close.
Enter the Channel 2 Latched command the receiver Channel 2 is Open, the Channel 1 is Close.
Enter the Channel 3 Latched command the receiver Channel 1 is Close, the Channel 2 is Close.
Delay: Enter the Delay command, the Rreceiver Relay is Open, delay of 0-9999 seconds(MODBUS command is 0-255 seconds )after, Relay is Close;
During the delay, Eter the Close command, immediately close the relay
Interlock between two channels: refers to the interlock between 1-2, 3-4, 5-6, 7-8, 9-10, 11-12 channels. Input channel 1 interlock command, channel 1 relay ”open”, channel 2 relay off; press input channel 2 interlock, channel 2 relay ”open”, channel 1 ”close”; input channel 3 interlock command, channel 3 relay ”Open”, channel 4 channel relay is closed; press input channel 4 to interlock, channel 4 relay ”open”, channel 3 ”close”; and so on
Slave ID: A0-A5 is the slave ID, you can choose 64 different slave ID.
Under the MODBUS command mode,the slave ID must be correct
command Description, Please refer to ” ETD8A12 12-channel RS485 IO input and output controller commamd”
1. The dial switch (slave address) is invalid and can only control one module at a time.
2. MODBUS command mode (HEX), you can control a variety of ways: Serial HyperTerminal Control (need to manually add the CRC), Modbus Poll software control (software automatically add the CRC), PLC or MCU process control